TokiLux may be specified in a variety of configurations for use in indirect lighting applications. All versions include a track fitted with Light Bars. Each Light Bar measures 8″ (200 mm). A single fixture can include from 1-12 Light Bars.
TokiLux Basic, WG and KT Light Bars consume 4 watts, and up to 12 Light Bars (48 watts) may be connected together. TokiLux RGB Color Bars consume 2.4 watts, and up to 12 Color Bars (28.8 watts) may be connected together.
Fixtures cannot be trimmed on site, so the overall length is based upon the number of Light Bars included. Check the sizes and lengths chart for precise measurements.
Conforming to Curves
TokiLux fixtures will not curve, but flex connectors can interconnect smaller sections to conform to curves as shown. In this case each length of TokiLux requires a minimum of two mounting brackets.
Leads on feed connectors are 6 ft. long. Additional lead wire may be spliced on by the installer
in order to reach remote LED driver locations. The distance from the fixture to the power supply and the load of the fixture will determine the proper size of secondary wire. This chart provides recommended distance of the secondary circuit using #18 AWG based upon the loads shown.
All systems are installed using mounting clamps, with the exception of TokiLux WG channel fixtures. Channel fixtures are supplied with clamps installed. Mounting clamps are screwed into place and concealed behind the fixture. Recommended spacing is 12″ on center.
Optional channels may be specified with fixed or adjustable mounting brackets to target and precisely focus light where needed. Fixtures are provided with brackets installed.